Fire Hose Care, Handling & Maintenance
North American Fire Hose Corporation is committed to providing the highest quality raw material, unique designs features, and special manufacturing methods in producing our attack line hose and large diameter hose. Our goal is to provide superior performance, low maintenance, and long service life.
The following care, handling, and maintenance guidelines were prepared to provide information to both first-time hose users, as well as to departments that are experienced in the use of hose lines.
Dragging Attack Line Hose or Large Diameter Hose (LDH)
Avoid dragging hose along its edge or fold, as this action concentrates abrasion of the outer jacket in the folded area. More
Loading Hose into the Apparatus Hose Bed
Only hose that is thoroughly dried should be reloaded in the hose bed and stored for a prolonged period of time. More
Special Precautions for Preserving the Hose Compartment and Hose
The hose should be loaded in a manner to allow for air to freely circulate between the hose bed and the hose to prevent rusting, corrosion or rotting of the hose bed. More
Storage of Fire Hose
All hose shall be kept out of direct sunlight and in a well-ventilated location. All hose shall be drained and thoroughly dried before being placed in storage. More
Coupling Damage due to Hose Deployment
Care must be taken when laying hose onto the street from a hose bed to prevent the couplings from being damaged by flipping up and striking the hand rail or by dropping too hard onto the apparatus tailboard or onto the street. Also, care should be taken to avoid dropping the couplings onto a hard surface when disconnecting the hose after use.
Hose bridges should be used whenever it is necessary for vehicles to drive over any fire hose, to prevent damaging either the couplings or hose.
When attaching the hose to a hydrant, allow for enough slack to permit a smooth bend radius from the hydrant. Also, open the hydrant slowly to minimize any water hammer effects.
Allow for enough slack in the hose to permit a smooth bend radius to the pumper connection.
Relay Applications for Large Diameter Hose (LDH)
When relaying water from a pumper near the water source to another pumper, the inlet or suction side of the pump receiving the relay should be equipped with a relief valve to reduce and control any water hammer effects. More
Reloading and Coiling Procedures - All Fire Hose
After shutting off all pumps and hydrants, but prior to breaking loose any of the couplings, the normal twisting that occur when the hose is pressurized should be removed. More
Inspection and Service Testing
The hose shall be inspected and service tested annually per NFPA 1962 Standard for the Inspection, Care, and Use of Fire Hose, Couplings, and Nozzles and the Service Testing of Fire Hose, Latest Edition. More
To maintain the Warranty provided by North American Fire Hose, repairs will be limited to coupling attachment replacements, provided the person conducting the repair has attended the Coupling Attachment Hands-on Instructional Class at North American Fire Hose's facility. More
- Who We Are
- Municipal Products
- Industrial Products
- Quality Driven
- Design Excellence
- Request Catalog
- Contact Us